Fire Code 901.6.1 for Maintenance Standards states that Fire protection Systems shall be
Inspected, Tested, Serviced and Otherwise maintained in accordance with this section, the rules and the referenced standards listed in Table 901.6.1.
Where required by this section 901.6.1, such inspection, testing and maintenance shall additionally comply with the rules.
Where applicable, the requirements of the reference standards listed in Table 901.6.1 shall be in addition to those requirements specified in the rules.
NYCTBM, INC. A Fireguard Company Please note: This material is information contained in the F-01 (City-Wide Fire Guard for Impairment) study guide